Sears is proud to be the dependable name in Upper Arlington, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
HVAC repairs can range between $100 and $600. Technicians typically charge between $100 and $250 for the initial service call.
If added repairs are required, they will charge an hourly rate of $50 to $100. Some contractors also charge flat rates, which can be advantageous if a project takes longer than expected. You will only be charged the quoted amount. However, other factors such as the size of your home, the time of year the repairs are required, and the cost of the parts required to repair your unit can all have an impact on how much you'll pay.
HVAC replacement costs can range from $5,000 to $10,000, which includes the installation of a new central AC unit and gas furnace combo as well as labor. If you also need to replace ductwork, expect to pay an extra $2,100 for a single-story 2,000-square-foot home.
A dirty heating system filter can cause the furnace to shut down. The primary trigger of furnace troubles is clogged filters. Dust and dirt obstruct airflow, and if the filter becomes too clogged, the heat exchanger overheats and shuts down too quickly, preventing your home from warming up. Replace the filter if the air compressor is running but no heat is coming out.
Find out why we've been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Upper Arlington, OH below.
for Upper Arlington, OH
Our Reviews by City
Eric - Upper Arlington, OH 43212
We recently moved back into the area and when it comes to anything related to HVAC our choice was simple! Sears Heating and Cooling! Professional, thorough, and made appropriate recommendations given the age of our furnace. Simple transaction and confident going into the Winter.
Michelle - Upper Arlington, OH 43221
Josh was great! Super knowledgeable and friendly. Will be using Sears again in the future for sure
Performed yearly maintenance and safety checks on Rheem furnace. Replaced 20255 filter as well as #35 water panel under service agreement. found 56 degree delta t. 11%o2 28 ppm co in flu 0 in supply no concerns at this time.
Diagnosed Trane air conditioner low on refrigerant perform leak check to find leak added refrigerant plus sealant plus Hardstark restored system for cooling purposes
Annual maintenance check on a rheem air conditioner
Performed air conditioning and furnace check on Bryant equipment
Made call for cooling upon arrival. Found system cycled on. Compressor failed to cycle. 40 voltage absorption system reading 0.003nf. Advised customer possible electric issues due to neighbor having same issues. Hn13a-e customer chose option d. Performed repair and cycled system. No further concerns at this time. 77 RA 57 SA.
Performed air-conditioning maintenance and safety check on Lennox unit
Diagnose evaporator coil frozen up unit is over 20 years old. Provided customer with estimate to replace system.
Returned to replace evap coil under warranty. Performed replacement , replaced filter drier. Triple evac below 500 charged up to manufactures specs. 79RA 51 SA. No concerns at this point.
Diagnosed American Standard unit low on refrigerant found leak at indoor coil.
Replaced failed blower motor and tested unit. All systems operating at this time.
Replaced bad condenser fan motor and fan blade
Performed air conditioner, maintenance and safety check on Bryant unit
14”- 45” is the inside opening of wall unit we will see if we can get something to fit in 20000btu output Wall unit will not keep pilot light the gas line has 2 shut-offs in line one at the crawl space in basement and one in unit I will speak to I stall and see if we can price one of these simpler system set up