Sears is proud to be the dependable name in Marble Cliff, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Marble Cliff, OH below.
for Marble Cliff, OH
Our Reviews by City
Great Service and Pricing.
Cynthia - Marble Cliff, OH 43212
Josh fixed the issue in no time at all. He arrived on time and happily and candidly answered questions with patience.
Megan - Marble Cliff, OH 43212
Josh was assigned to my service today. He was on time, professional and very kind.
Response from Sears Heating & Cooling:
Thanks so much! We will show this to Josh.
Completed annual maintenance on a 2010 Ducane air conditioner. All mechanical components of the system check out at this time. During testing of the unit the technician found the initial amp draw of the compressor to be outside of manufacturers specifications. Technician also found there was no electrical protection device for the outdoor unit. Technician presented options hn1a-e. Customer declined any repair at this time and will readdress the situation come spring.
Drain line is plugged. Went over options on page ho1. Customer chose ho1a. Cleared obstruction from drain line with Nitrogen. Strapped all connection for drain hose with zip ties for secure and tight seal. Flushed gallon of water through drain line without issues and no leaks. All okay at this time.m
Concern was the system was not cooling Found bad on hermetic system side Chose bottom option Also I had a concern with system needing of cleaning There is a water valve outside by ac but it is not working The 4 garages in front I believe have the shut off in. Believe it’s the first one. She inquired on cleaning. I explained best if she speaks to the neighbor with the first garage I brought up the benefits of the service contract and a time to schedule with the water access available We do have a water cleaning system but that will have to be scheduled with the contract and it does not clean as well as actual water from city water
Returned with sensor but the sensor I brought would not work to replace the current sensor. Went ahead and ran a combustion test while I was here and found water heater burning off over 1200 ppm of CO. Pool burner assembly and found large amount of buildup and dirt in the burners. This is what’s causing the sensor to trip. Cleaned out burner Assembly and reinstalled. Unit is now burning 22 ppm. All OK at this time.
2009 Maytag gas furnace. Found concern with flame sensing system. Flames going out very intermittently. Tried cleaning it and still have issue. Recommended replacing flame sensing system. Showed options on page hm15. Customer chose hm15a. Completed repair and cycled unit. Unit is very clean on the inside and customer keeps up with filters. Performed combustion analysis. 39 ppm CO/ 8.4% O2/ 399 degree stack temp. All okay at this time.
Performed furnace maintenance and safety check on Bryant u it. Serviced humidifier for heating season
Maintenance check on furnace concord 2001. hvac tune up in grandview, ohio.