Plain City has grown exponentially over the past few years. Driving through the countryside you will see many new up and coming neighborhoods. Conveniently located just a few minutes from Columbus, Plain City has become a popular location to build both a home and a family. One of the most popular restaurants located in the area is the Amish restaurant, Der Dutchman. The city is well known for its agricultural heritage.
You can always count on Sears Heating and Cooling in Plain City, OH for respectful, professional and reliable HVAC services. Check out the local reviews below to see why we are so highly recommended!
Heating and air conditioning equipment should be examined, cleaned and serviced at least twice a year, regardless of the kind. The optimum time is to have the heating and air conditioning systems inspected in the fall and spring, respectively. Regular maintenance ensures that your HVAC equipment is operating properly, saving you money on wasted energy, excess repairs and early replacements.
Some HVAC repair firms charge fixed fees for their various HVAC services. Other businesses bill on an hourly basis - typically between $150 and $200 per hour. The costs of the technician, the expense of their travel and the value of the service they provide are all included in the per-hour rates. Sears Heating and Cooling will only charge you for services you actually need; you never need to worry about inflated bills when working with us.
Manufacturers recommend replacing basic 1"–3" air filters every 30–60 days. If you have light to moderate allergies, you should upgrade your air filter or change it more frequently. Check your filters every month to see how dirty they are and if they’re ready to be changed.
for Plain City, OH
Our Reviews by City
Bill - Plain City, OH
Josh did a great repairing my air conditioner. Highly recommend this company.
Lauren - Plain City, OH
Ramon is genuinely the best tech I’ve ever had help us before. He really takes his time to explain things to me and makes sure I understand what is happening in addition to how all products work as I typically have a lot of questions haha. Truly, your best employee.
Response from Sears Heating & Cooling:
Thanks so much! We will show this to Ramon and the team!
2013 Bryant high efficiency 2 stage gas furnace. Circuit board showing reverse polarity code, the calling for heat as normal when I arrived.mi shut system down and jumped out but did not get an immediate call for heat, system turned on after roughly 45 seconds when it should have been instantaneous. I reset and tried again, getting 28 v between w and c but not getting immediate call for heat. Circuit board is failing. Went over options on page he1. Chose he1a. Completed repair. Cycled and tested. Combustion results good. All okay at this time.
Performed furnace maintenance and safety check on Trane unit. Serviced humidifier for heating season
Performed furnace maintenance and safety check on Rheem unit. Replaced leaky furnace condensate trap.
Performed air conditioner maintenance on Lenox
Performed furnace maintenance and safety check on York unit
Restored furnace to clean condition
Performed air conditioner maintenance on Bryant unit
Performed air conditioner maintenance on Goodman unit. Replaced failing capacitor and hard start
Provided estimate to move AC condenser over 5 feet.
Replaced leaky evaporator coil, inspected Aprilaire digital ventilation system
Found leaky Evaporator coil, provided temporary cooling
Performed air conditioner maintenance on York unit
Performed furnace maintenance and safety check on Goodman furnace . Serviced Aprilaire humidifier for heating season.
Performed furnace maintenance and safety check on Bryant furnace
Furnace upstairs, there is a leak out of the trapping system, Lennox. There is not back up drain line and the safety system is not wired in. Concern of Greg’s was that there is water build up in the summer time on furnace. Lines could be sealed better, Hf-5 Basement furnace The trapping system is leaking on floor and water dripping on furnace in cooling There is a popping in the supply duct due to not having cross lines will have to add S lock and make lines that are inverted. Hf-5 Wp 35 was very bad replaced Monday is a good day to return to do repairs Furnaces are form 2017 Lennox 90% systems one stage up stairs and downstairs but down stairs has two zones thermostat is next to furnace in basement for zones and main stat is on pillar before going downstairs Co in home is 0ppm but there are multiple fire places running and can lead to co in home Flame sensing systems are clean and no electrical issues in furnaces
Diagnosed furnace repair needed as failed control board. Ac repair cannot be completed today as manufacturers are not available. I will return Monday to complete repair.
2014 rheem furnace. Water at the bottom of furnace and coming out of the back onto basement floor. Found clog in condensate drain. Offered options for flush and to add water safety switch. Showed options on page hf3. Chose hf3a. Flush line and added total tabs. Poured 4 bottles of water through line and now draining great. Cycled system. All okay at this time.
Removed blockage in condensate drain trap
Inspect AIr conditioner for loud operation