Sears is proud to be the dependable name in Grove City, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Grove City, OH below.
for Grove City, OH
Our Reviews by City
Trevor - Grove City, OH 43123
Nick - Grove City, OH 43123
Josh did my annual check up on furnace and also installed a humidifier. Josh thoroughly explained humidifier operation and it’s effectiveness. Excellent service.
Brenda - Grove City, OH 43123
Great service and price !
Ken - Grove City, OH 43123
Andy - Grove City, OH 43123
Enjoyed talking Hvac with our sears rep!
Performed yearly maintenance and safety checks on 2022 Bryant furnace. Found 15 ppm co in flu 0 ppm co in supply. 76 RA 126SA 50 degree delta t. Left new 16251 filter. Cleaned flame sensor 56 ohms on ignition system No concerns at this point in time.
Performed yearly maintenance and safety checks on 2022 Bryant furnace. Found 15 ppm co in flu 0 ppm co in supply. 76 RA 126SA 50 degree delta t. Left new 16251 filter. Cleaned flame sensor 56 ohms on ignition system No concerns at this point in time
Customer has noise complaint with air conditioning unit. Vibration can be heard in bathroom. found 2007 410 system on house stand, also found lineset strapped tight to floor joist. Vibration from unit and lineset causing noise. Advised customer with 16 year old system risk are present with cutting into and dropping condenser to ground no Warranty with repair and Additional parts. HO11 $2156 is page for repair. Provided quotes for new 4 Ton air conditioning systems. Bryant 4 ton systems out of stock at this point in time. Supplied both Bryant and American standard quotes for customer. Customer will review with wife and reach out when decision is made.
73 RA 120 Sa Cleaned flame sensor Left new 20251 filter. 15 voltage absorbsion system reading 15. 9%o2 113° 18 ppm co in flu. 0ppm Co in supply. Blew out drain. No sign of gas leak via electronic detector Replaced #35 water panel, set humidistat to 35 no concerns at this time.
Replaced failing capacitor on Bryant air conditioner inspected upstairs area for installation of return docs to improve room comfort
Performed yearly maintenance and safety checks on ARCOAIRE air conditioning system. Found 69 RA 52 SA. found 27.5/5 voltage absorption system reading 25/4.9. No sign of overheating or pitting inside disconnect or voltage distribution system
Performed ac service and safety checks on goodman air conditioning system. Found no overheating inside disconnect or on voltage distribution system. Found 45/5 voltage absorption system reading 38.8/4.8. No hard start or surge protection on system. Informed customer of concerns hn15 customer chose option a. Performed repair cleaned system added tabs, 20251 filter. No concerns at this point in time.
Performed yearly maintenance and safety checks on 2003 Trane air conditioning system found coil to be super dirty 16251 filter35/5 voltage absorption system reading 34.5/5. No signs of overheating on voltage distribution system or disconnect. R22 system. Informed customer of age and restrictions with refrigerant. No concerns at this time
Performed yearly maintenance safety checks on 2011 Rheem air handler heat pump system sound system low on charge, what is absorption system outside manufacture specifications rated 40/5 reading 35/5 sound voltage distribution system burns showing signs of age and overheating. Found compressor had bad rattle noise. Customer stated ice has been built up around the unit in past. System has small leak previously noted did not specify whether internal leak sealant was used informed customer of issues risk and overall situation customer interested in new system sales person Heading out now to give a quote for replacement customer decided to stay on service plan for today.
Thermostat Repair - Replaced faulty, thermostat cycled heating and cooling systems. System comfort return to operation.
Cost to install furnace and air conditioning. Furnace is up in the attic. Cost to replace furnace in attic.