Sears is proud to be the dependable name in Grove City, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Grove City, OH below.
for Grove City, OH
Our Reviews by City
Trevor - Grove City, OH 43123
Nick - Grove City, OH 43123
Josh did my annual check up on furnace and also installed a humidifier. Josh thoroughly explained humidifier operation and it’s effectiveness. Excellent service.
Brenda - Grove City, OH 43123
Great service and price !
Ken - Grove City, OH 43123
Andy - Grove City, OH 43123
Enjoyed talking Hvac with our sears rep!
Performed yearly maintenance and safety checks on ARCOAIRE air conditioning system. Found 69 RA 52 SA. found 27.5/5 voltage absorption system reading 25/4.9. No sign of overheating or pitting inside disconnect or voltage distribution system
Performed ac service and safety checks on goodman air conditioning system. Found no overheating inside disconnect or on voltage distribution system. Found 45/5 voltage absorption system reading 38.8/4.8. No hard start or surge protection on system. Informed customer of concerns hn15 customer chose option a. Performed repair cleaned system added tabs, 20251 filter. No concerns at this point in time.
Performed yearly maintenance and safety checks on 2003 Trane air conditioning system found coil to be super dirty 16251 filter35/5 voltage absorption system reading 34.5/5. No signs of overheating on voltage distribution system or disconnect. R22 system. Informed customer of age and restrictions with refrigerant. No concerns at this time
Performed yearly maintenance safety checks on 2011 Rheem air handler heat pump system sound system low on charge, what is absorption system outside manufacture specifications rated 40/5 reading 35/5 sound voltage distribution system burns showing signs of age and overheating. Found compressor had bad rattle noise. Customer stated ice has been built up around the unit in past. System has small leak previously noted did not specify whether internal leak sealant was used informed customer of issues risk and overall situation customer interested in new system sales person Heading out now to give a quote for replacement customer decided to stay on service plan for today.
Thermostat Repair - Replaced faulty, thermostat cycled heating and cooling systems. System comfort return to operation.
Cost to install furnace and air conditioning. Furnace is up in the attic. Cost to replace furnace in attic.
Performed furnace check for heating operation
Performed yearly maintenance and safety checks on 2005 Bryant air handler heat pump system. Full communicating system. Ran checkout through stat. Found 21 amps per circuit. 15 kw heat kit. .44 static in high heat .18 TESP IN HP HEAT. 18 degree delta t. Thermostat cycled through modes correctly and within manufacture specifications customer opted for humidifier coverage. Changed #10 wp. No concerns at this time.
Upon arrival customer stated she sets temp to 68 at night and 70 upon waking for the day. Stated she’s changed temp to 70 furnace never kicked on temp inside house went lower about to 66. Found codes 10 11 12 being thrown. Ignition failure 1 hr lockout and low flame sense. Recycled furnace to find furnace faultingse mode after startup. SC customer. Technician did scfc 10/10/22 found excess residue on sensor. Replaced sensor under sc membership. Service charge only today. Cycled furnace multiple times without fault . Found 9.2 o2 15 ppm co. 0 in supply. 50 degree delta t. No concerns.
Inspected oil furnace for fuel oil smell
Replaced plugged furnace filter found returned duct full of drywall dust working with customer on estimate to replace return duct
Diagnose faulty flame sensing system for fireplace
Performed yearly Maintenance and safety checks on2013 Rheem 90% furnace. Found inducer motor pulling .47 amps. Rated .5. Cleaned washable filter. Found 0 ppm co with ambient test. 29 ppm co in flu with 87 degree stack temp. 1.8inwc gas pressure. 72 RA 109 SA 37 degree delta t .44 TESP in low fire. 18PPM ppm co in flue with 93 degree stack temp. 3.4 in wc gas pressure. 74 RA 125 SA 51 degree delta t. .42 TESP in high fire.found one concern with gas line. Furnace does not have dedicated drip leg. Picture uploaded. Thermostat stealing 0.0 volts quoted Sh3a-e customer rejected repairs at this time. Informed customer of purification and humidifier systems. Customer will wait for accessories
Performed yearly maintenance and safety checks on 2020 Bryant 80% furnace. Found ignition system reading 47 ohms thermostat stealing 0 V 0PPM co in flu 24 in flu system is running properly and within manufacture specifications at this time with no cause for concern
Returned to complete repair hd5b. Performed repair. 10kw heat kit. Both circuits pulling 20 amps. No concerns