Sears is proud to be the dependable name in Grove City, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Grove City, OH below.
for Grove City, OH
Our Reviews by City
Trevor - Grove City, OH 43123
Nick - Grove City, OH 43123
Josh did my annual check up on furnace and also installed a humidifier. Josh thoroughly explained humidifier operation and it’s effectiveness. Excellent service.
Response from Sears Heating & Cooling:
We are so grateful for your 5-star review. Thanks for sharing your rating with us and the community.
Brenda - Grove City, OH 43123
Great service and price !
Ken - Grove City, OH 43123
Andy - Grove City, OH 43123
Enjoyed talking Hvac with our sears rep!
Customer had concern with leaking humidifier. Stated that black buildup caused blockage in clear tubing. Customer removed and cleaned with pipe cleaners. Asked if issue is normal. Advised slight buildup and discoloration is normal but not a full clog. Inquired about hard water. Customer stated water filtration system had issues, advised those issues could cause worse buildup then normal pad quite used replaced in august but looks as if hadn’t been replaced in multiple years. Advised filter issues seems to be cause. Customer has issues with dryer vent. Dryer is in pamper room with vent inside wall. Wanted hard pipe to wall inlet. Advised dryer would need to be moved out to hard pipe. Roughly 4-5 inches pulled dryer out as rough ballpark. Customer was not satisfied and looking into a more rigid flex pipe to avoid buildup in pinched pipe., customer has insufficient return air upstairs. Interested in mini split installed in main hallway foyer to accommodate in heating and cooling seasons.
Annual maintenance check on a Bryant heat pump
Performed yearly maintenance and safety checks on 16 rheem furnace. Found 10%o2. 14 ppm co in flu. 0 ppm co in supply. Left new 16251. Customer opted for humidifier coverage. Upon startup humidifier failed to cycle. Found very slow drip from water supply. Saddle valve opened up with little persuasion. Humidifier properly cycled on and off through humidistat, 55 degree deltat.
Rheem 90% 2014 Filter 413-410 Flame sensing system is clean Trapping systems are good Electrical is secure Wp 10 and is all set up for winter Comin flue is 19 ppm good I changed her controller back to the existing due to better ability to use and inspection is over She will save t4 Filter is clean
Performed yearly maintenance and safety checks on 2022 Bryant furnace. Found 15 ppm co in flu 0 ppm co in supply. 76 RA 126SA 50 degree delta t. Left new 16251 filter. Cleaned flame sensor 56 ohms on ignition system No concerns at this point in time.
Performed yearly maintenance and safety checks on 2022 Bryant furnace. Found 15 ppm co in flu 0 ppm co in supply. 76 RA 126SA 50 degree delta t. Left new 16251 filter. Cleaned flame sensor 56 ohms on ignition system No concerns at this point in time
Customer has noise complaint with air conditioning unit. Vibration can be heard in bathroom. found 2007 410 system on house stand, also found lineset strapped tight to floor joist. Vibration from unit and lineset causing noise. Advised customer with 16 year old system risk are present with cutting into and dropping condenser to ground no Warranty with repair and Additional parts. HO11 $2156 is page for repair. Provided quotes for new 4 Ton air conditioning systems. Bryant 4 ton systems out of stock at this point in time. Supplied both Bryant and American standard quotes for customer. Customer will review with wife and reach out when decision is made.
73 RA 120 Sa Cleaned flame sensor Left new 20251 filter. 15 voltage absorbsion system reading 15. 9%o2 113° 18 ppm co in flu. 0ppm Co in supply. Blew out drain. No sign of gas leak via electronic detector Replaced #35 water panel, set humidistat to 35 no concerns at this time.
Replaced failing capacitor on Bryant air conditioner inspected upstairs area for installation of return docs to improve room comfort
Performed yearly maintenance and safety checks on ARCOAIRE air conditioning system. Found 69 RA 52 SA. found 27.5/5 voltage absorption system reading 25/4.9. No sign of overheating or pitting inside disconnect or voltage distribution system