HVAC Repair & Replacement Services in Galloway
Sears is proud to be the dependable name in Galloway, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Galloway, OH below.
for Galloway, OH
Our Reviews by City
MARY - Galloway, OH 43119
Service was great as always.
Mary - Galloway, OH 43119
Harry - Galloway, OH 43119
Josh was great
Response from Sears Heating & Cooling:
Thank you for your review!
Set electrodes?: Yes Checked oil pump pressures?: Yes Checked limit safety?: Yes Checked primary control?: Yes Checked furnace vent for rust?: Yes, I did. None present. Checked draft overfire: Yes Returned furnace to service?: Yes Does the customer have a Humidifier?: No
Blower motor had failed on Trane furnace. Due to age a Furnace customer decided to replace. We are installing a Bryant furnace on Monday.
Diagnosed low voltage interruption from transformer
Made call for cooling upon arrival. Indoor system cycled on outdoor system failed to cycle. Upon taking over electrical cover spotted multiple ear wigs falling and scurrying away, unit started up immediately after. Found concern with slide having bigger then normal ark flash upon connecting.. pulled low voltage to test ark flash multiple times. Significant flash every time. Customer had part replaced with 1 year warranty that ended in march 23. Advised fault possibly due to bugs getting into slide area. Also could be having issues with slide getting stuck. Explained Concern with switch welding itself shut with ark flash. Hd3 customer chose option a. Performed repair and cycled system. System is running properly at this point in time.
Diagnosed faulty, furnace blower motor in Trane unit
Provided repair options for repairing leak in heat pump system also provided replacement estimate for heating and cooling equipment
Left estimate and took measurements for furnace replacement. Reviewed financing options with customer.
Customer heard humming at outdoor system. Said smoke came from system. Found reversing valve clicking rapidly. Compressor blew. Will need quote for new system
Found furnace in lockout reset system to find control board sending 69-72 volts to ignition causing failure customer wants called for quoting Monday.
Performed furnace maintenance and safety check on Goodman unit
Replaced main control board high limit switch on train unit
Diagnosed week high limit switch and failing blower motor and training furnace