HVAC Repair & Replacement Services in Galloway
Sears is proud to be the dependable name in Galloway, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Galloway, OH below.
for Galloway, OH
Our Reviews by City
MARY - Galloway, OH 43119
Service was great as always.
Mary - Galloway, OH 43119
Harry - Galloway, OH 43119
Josh was great
Response from Sears Heating & Cooling:
Thank you for your review!
Performed furnace maintenance and safety check on Goodman unit
Replaced main control board high limit switch on train unit
Diagnosed week high limit switch and failing blower motor and training furnace
Completed mechanical, safety, and performance test on air conditioner. Found concern with voltage enhancement system being out of Manufacturers specifications and weak. Also found voltage distribution center has pitted contacts and starting to causing burning and charring. Went over options on page hn13. Chose hn13 c to do both repairs. Replaced faulty voltage enhancing system and upgraded to turbo enhancing system. Replaced burnt distribution system. Cycled and tested. All okay at this time.
Performed furnace maintenance and safety check on Bryant unit. Provided estimate for steam, fan powered and by-pass humidifiers.
Replaced failed contactor and cleaned up wiring terminal ends
Replaced faulty capacitor, hard start kit and water protection system for second floor mechanical room installed
2019 York air conditioner. Unit has thawed. Check pressures and they are good. All electronics are within specs unit is 2 years old. Customer mentioned they had changed the filter before I came and it was very dirty. Dirty filter caused lack of airflow causing the coil to freeze and with it being as frozen as it was unit need to that before running it after changing the filter. Temp split is 18 degrees. Let customer know to change filter one a month. All okay at this time.