HVAC Repair In Grandview Heights, Ohio
Sears is proud to be the dependable name in Grandview Heights, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Grandview Heights, OH below.
for Grandview Heights, OH
Our Reviews by City
Replaced burnt wirie and contactor
Condensate trap has massive clog backing water up into secondary heat exchanger. Recommended get a combustion analysis performed on system, 23 year old infinity. Went over options on page hk5. Chose hk5a. Cleared trap and tuned up system. Completed combustion test and results are good. System is operating safely and efficiently. All okay at this time.
Performed furnace maintenance and safety check on Bryant unit
System is low on charge r22 Bottom option chosen, does realize the system is of age of replacement but want to fill and see how long this will last first time leak Lennox 1987 and is making not the greatest noise due to compressor Filter is clean 79/226 psig Bella is great
2016 Bryant air conditioner. Completed mechanical, safety, and performance test on air conditioner. All okay at this time. Customer interested not the iwave. Discussed benefits with her and gave her a brochure. She wanted to have installed today. Showed her how to set blower fan to continuous to get max results from iwave.
2019 American standard gas furnace and aprilaire 600m humidifier. Found saddle valve closed not allowing water to pass into humidifier solenoid. Adjusted water flow for humidifier and tested unit. Set humidistat at 35%. Performed combustion analysis on furnace. Ppm co 8/11% o2/flue temp 94 degrees. Discussed with customer operation of humidifier. He mentioned he did. It close the saddle valve and was unaware it was there. Saddle valve is set where it needs to be and does not need to closed during off season. Only turn off humidistat and close bypass damper. All okay at this time.