Sears is proud to be the dependable name in Upper Arlington, OH for everything heating and cooling related. Our highly-skilled professionals have what they need to tackle any job, diagnose any problem and complete any repair. Your comfort is our number one priority.
Find out why we’ve been held in such high esteem since we were founded in 1950. Read reviews from the good folks of Upper Arlington, OH below.
for Upper Arlington, OH
Our Reviews by City
Eric - Upper Arlington, OH
We recently moved back into the area and when it comes to anything related to HVAC our choice was simple! Sears Heating and Cooling! Professional, thorough, and made appropriate recommendations given the age of our furnace. Simple transaction and confident going into the Winter.
Michelle - Upper Arlington, OH
Josh was great! Super knowledgeable and friendly. Will be using Sears again in the future for sure
Called for cooling oudoor unit cycled on properly. Indoor unit faulted and blower failed to run. Found proper voltage going to blower informed customer is issues customer stated with age of system he is interested in replacement. Scheduled for Tuesday morning
Diagnosed faulty condenser fan motor
Performed air conditioner maintenance on Carrier unit
Technician returned to complete repair. Performed repair and cycled unit multiple times. 55 degree delta t. 0 co in supply. Cycled unit with jumper at control board. Unit cycled on and off properly. Cycled unit multiple times through thermostat to ensure proper operation. Unit cycled each time properly without fault or concern. No further concerns at this time.
Upon arrival system was showing code 3 for pressure switch issue, technician preformed diagnostic steps to find board not properly distributing voltage to turn on combustion exhaust system customer wanted to open up a supply house after hours however found no answer at any supply houses. Will call back tomorrow with pricing and availability.
Replaced Trane furnace main limit
Diagnosed faulty high limit switch.
Customer mentioned new system having issues. Doesn’t want to come on when calling from thermostat at times. I found venting drooping in a long run and holding water causing a code 32 for pressure sensors not closing or reopening. I drained water from pipe and put in more strap to obtain a better drop to allow water to flow into furnace. Gasket connection between flue and inducer was leaking. Corrected and set in place and tighten all clamps. No longer leaking water. Changed water panel 12 for humidifier. When testing found small pinhole leak in feeder tube and leaking water onto the floor. Went over on page sh3. Chose sh3a. Replaced feeder tube system and adjusted water pressure and tested. All okay at this time. Completed mechanical, safety, and performance test on furnace. All okay at this time.
Serviced flame sensor and circuit board replaced.
Thermostat is low located in bedroom directly next to bathroom with heated floors. Discussed with customer and agreed on moving to hallway near living room. Unable to use current thermostat and equipment module as it requires a three wire configuration to communicate. Went over options on page hh28 to install red link module and vision pro 8000 full wireless thermostat. Chose to go with hh28c. Completed repairs and cycled furnace. Completed performance testing. Combustion analysis good. All okay at this time.
Performed air conditioner maintenance on Bryant units