Serving Upper Arlington, Ohio since 1950
Sears Heating & Cooling is proud to be the dependable name in Upper Arlington, Ohio for everything heating and cooling related. We provide HVAC repair as well as installation services. Find out why we’ve been held in such high esteem since we were founded in 1950 from our Upper Arlington, Ohio customer reviews below.
for Upper Arlington, OH
Our Reviews by City
Michelle - Upper Arlington, OH
Josh was great! Super knowledgeable and friendly. Will be using Sears again in the future for sure
2016 rheem air conditioner. Completed mechanical, safety, and performance test on air conditioner. Found concern with high inrush current to compressor. Recommended adding performance kit reduce inrush current, prevent damage to compressor motor winding and increase compressor life. Showed options on page hn1. Hose hn1a. Completed repair. Amps dropped from 74 to 44. All okay at this time.
2018 rheem air conditioner. Completed mechanical, safety, and performance test on air conditioner. All okay at this time. Customer Mentioned him and his family have allergies all year around and was looking for some Ways to help control allergens Inside the home. Discussed benefits of a iwave air purification system and left a brochure. He also mentioned filters get dirty very fast. I recommended having the ducts cleaned and gave information for fresh air Corp As well as possibly upgrading his filter cabinet. He does have room to move the return duct and install April air filtration system. Customer wants to research a bit more into the iwave, let him know to give us a call if he decides he wants to have one put in.
Performed furnace maintenance and safety check on Two Bryant furnaces .serviced humidifier
Replaced spark control on a Lennox furnace.
Furnace check on Lennox. 2006 90% PCs motor. 20-25-4 filter. Ac on roof
Completed air conditioner clean and maintenance checks on Bryant systems
Air conditioner maintenance clean and check
2000 concord furnace. Water leaking into furnace. Found condensate drain clogged in multiple places. Offered options for replacing drain line on page ho2. Chose ho2a. Replace pipe and flushed condensate pump. All okay at this time.
Complete mechanical, safety, and performance test on air conditioner. Found start up module for performance kit dead. Compressors start amps are higher than max. Recommended replacement of performance kit to drop inrush current to compressor. Provided options on page hn1. Customer chose Hn1c. Installed new performance kit and upgraded voltage absorption system. Renovated electrical terminations. Cycled unit. All okay at this time.
Performing maintenance on 2 2012 Bryant air conditioners and a mr. slim ductless mini split system. Found bad capacitor on one of the air conditioners. Unit covered under parts and labor warranty. Customer picked basic repair. Completed repair and tested unit.
Drain Line was clogged. I repaired and co2 flushed Found temp split low and made adjustments on air flow. Delay on controller multiple times Low and high stage cooling both working. Air conditioner repair.