Providing 100% Relief Since 1950!
Whether you are looking for hvac repair or installation you will find out why we’ve been held in such high esteem since we were founded in 1950 from our Grove City, OH customer reviews below.
When Do I Need a Repair?
There are a few different signs that could signal that it’s time for a repair on your heating and cooling system. Some of the most popular signs include:
- Not cold or hot air being produced
- Strange noises
- Strange odors
- Water leaking from your furnace
If you are experiencing any of these issues, your best bet is to first check your furnace filter to see if it is still clean. A dirty filter is the most common contributor to furnace and air conditioner breakdowns. If your filter looks ok, it’s best to call a professional HVAC company to come and take a look.
for Grove City, OH
Our Reviews by City
Great service and price !
Ken - Grove City, OH
Andy - Grove City, OH
Enjoyed talking Hvac with our sears rep!
Completed mechanical, safety, and performance test on furnace. All okay at this time. Customer mentioned unit not cooling. Found unit low on charge. Locking schrader cap laying on the ground appearing there could have been someone messing with the unit. Tested for leaks and found no leaks with detector and bubble solution. Offered options for nitrogen leak test on page ho1 as well as to charge the unit on page hj7. Customer would like to just have the unit charged at this time. Charged system to 11 degrees sub cooling. 20 degree temp drop. All okay at this time.
2008 Bryant air conditioner not cooling and requiring ac repair. Found unit very low on refrigerant charge. Large amount of corrosion on evaporator coil. Tested for leaks and found leak to be in the evaporator coil. Offered options on page hl1 for repair. Customer would rather have an estimate and look to replace the ac system. Jamie scheduled today around 3:15.
Concern with systems voltage absorption system not engaging the main pump Showed repair page and chose silver System is from 2007 R410 Replaced voltage absorption system Added performance kit Cleaned outdoor unit Added suction line insulation and silicone to opening Super heat 17 Lucy is great System is up and running good ac repair
Furnace and ac is from 2008 and temp star product. 90% with 12 seer ac Suction line insulation is new and pressures are good 74/198 superheat 12 Filter clean 16-25-1 No co in home Co in flue is 13ppm, good and no co in home. Wiped down furnace and cleaned outdoor coil. Furnace is 95% Cleaned trapping system out and flushed Electrical is good Outdoor voltage absorption system is 45/5 and is showing 44.7/4.9 Distribution system is good No hvac or ac, furnace repair needed at this time
Chauncey pup We spoke about IAQ via humidity and she will want me to repair humidifier for winter operations in fall check up Filter is clean 12-24-1 2003 trane Temp split is 18 Suction line good Piston Outdoor unit clean Electrical is good 30/3@30/3 mfd Added tabs to drain line
Ac is from 2003 r22 Cleaned outdoor coil Pressures are good Cleared brush away from ac Filter is clean 16-25-1 left one behind Loves John Wayne No ac repair is needed Electrical in system has been updated Hvac systems are good Added tabs to drain line Piston
Replaced burned up Contactor
Contactor and capacitor high voltage wires and terminal connections burned up and melted.
AC check out on a 2014 Bryant air conditioner. Completed performance check, safety check, mechanical check. Everything is working properly at this time.
Installed water tank and expansion tank found no leaks explain to Nick how to operate and how it works he is financing have a good day Mike and Ike
Air conditioner tune up in grove city, ohio.
Goodman air conditioner. Found voltage absorption system blown. Quoted repair on page hn5. Customer chose Hn5a. Cycled unit and checked charge. Found charge low. Tested for leaks with leak detector and did not get any reading, very small leak in the system. Offered options on page hj1. Customer chose hj1c. Installed hard start kit. Charged system to 12 degrees sub cooling and inserted leak seal. Cycled unit. 21 degree temp drop. All okay at this time,