Providing 100% Relief Since 1950!
Whether you are looking for hvac repair or installation you will find out why we’ve been held in such high esteem since we were founded in 1950 from our Grove City, OH customer reviews below.
When Do I Need a Repair?
There are a few different signs that could signal that it’s time for a repair on your heating and cooling system. Some of the most popular signs include:
- Not cold or hot air being produced
- Strange noises
- Strange odors
- Water leaking from your furnace
If you are experiencing any of these issues, your best bet is to first check your furnace filter to see if it is still clean. A dirty filter is the most common contributor to furnace and air conditioner breakdowns. If your filter looks ok, it’s best to call a professional HVAC company to come and take a look.
for Grove City, OH
Our Reviews by City
Trevor - Grove City, OH
Nick - Grove City, OH
Josh did my annual check up on furnace and also installed a humidifier. Josh thoroughly explained humidifier operation and it’s effectiveness. Excellent service.
Brenda - Grove City, OH
Great service and price !
Ken - Grove City, OH
Andy - Grove City, OH
Enjoyed talking Hvac with our sears rep!
Found air movement system completely failed. System is a thermal zone brand. Contacted rheem supplier and United refrigeration incorporated. Unable to find any information on the system to get parts. This brand was bought out several years ago and started getting manufactured by rheem and the no longer make parts for the older systems. Jamie scheduled for estimate tomorrow between 9am and 10 am.
1996 York air conditioner. Found system low on r22. Customer wants to just get unit by this year and is looking to replace full system next year. Went over options on page hj1. Chose hj1a. Charged system to 12 degrees superheat. Delta t is 17 degrees. Let him know when he is ready to replace to give us a call for an estimate. Discussed with him that we do have financing options.
2016 rheem air conditioner. Completed mechanical, safety, and performance test on air conditioner. Found condenser fan motor leaking large amount of oil. Fan blade is rusted to shaft of motor and will not come off. Customer has parts warranty and can receive $245 off of repair plus their 10% discount for service club. Showed options on page hc7 b-e. Chose hc7b. Completed repair and cycled unit. All okay at this time.
1990 Lennox air conditioner. Completed mechanical, safety, and performance test on air conditioner. All okay at this time. Concern with hot water tank. Pipe coming in is very corroded and can potentially burst at some point. Tank is also leaking from pressure relief valve. Also butterfly valve for outside spigot shutoff leaking. Discussed concerns with customer. His son is a plumber and he is going to have him take care of it.
2020 comfortmaker air conditioner. Completed mechanical, safety, and performance test on air conditioner. All okay at this time. Customer mentioned filter cabinet door is to low and scrapes on the rafter when changing the filter. I attempted to cut a small amount of the door to resolve issue but filter door broke off. Bent and installed new filter door and taped with small amount of insulation tape to keep door nice and shut tight to prevent bypass airflow.
Ac check on a Goodman with known leak in coil. System is low again and I wrote up quote
AC check on a 2004 Air conditioner. Completed performance check, safety check, mechanical check. Everything is working properly at this time.
Lennox gas furnace. Customer head reset furnace at breaker. Cycled unit a couple times without issue. When testing again furnace tripped on high limit. Found issue to be with plugged air filter. Customer said he would go ahead and change the filter. I recommended filter to be changed every 30 days to prevent this issue from happening again on the future.