Providing 100% Relief Since 1950!
Located a few miles outside of the outer belt on the west side of the city, Galloway, Ohio was built on land that was originally owned by a Revolutionary War veteran. The area is known for it’s vast farming land and parks including Battelle Darby Creek Metro Park.
Sears Heating & Cooling is proud to be the dependable name for HVAC repair in Galloway, Ohio. Find out why we’ve been held in such high esteem since we were founded in 1950 from our local reviews below.
Common HVAC Repairs
Although there are many different things that can go wrong with your heating and cooling system, there are several issues that we deal with more than others. These troubles include strange noises or smells, no hot or cold air being produced or water leaks inside. Be sure to check your filter on a regular basis to ensure it’s not contributing to the problem. The number one cause of HVAC breakdowns is dirt and debris.
Are Your Repairs Warrantied?
Of course! Each heating and cooling repair that we complete comes with a warranty to give you peace of mind. The length of warranties offered range from 30 days all the way up to 2 years.
for Galloway, OH
Our Reviews by City
Harry - Galloway, OH
Josh was great
Response from Sears Heating & Cooling:
Thank you for your review!
2006 carrier air conditioner needing ac repair. Customer mentioned unit was freezing up. Left off through the night. Found unit low on charge. Found Schroeder core slowly leaking refrigerant. Offered option on large hj1 for repair. Customer chose hj1a. Charged system to 11 degrees sub cooling and replaced Schrader core. Cycled unit. 19 degree temp drop. All okay at this time.
Troubleshooting a failed capacitor on a carrier air conditioner
Troubleshooting a comfort maker HVAC system after a main incoming power issue to house.
2014 comfortmaker air conditioner. Customer mentioned unit was freezing. Filter clean. Check refrigerant charge and found unit severely low. Tested for leaks and found leak to be in evaporator coi. Offered options for repair on page hl1 and hj7. Chose hj1a. Replaced coil and liquid line filter drier. Pressure tested system with nitrogen at 260 psi and half for 10 minutes. Vacuumed system down to 430 microns. Charged system to 10 degrees sub cooling. Cycled unit. All okay at this time.
Indoor air movement system is running but it’s starting to fail. Chose bottom option and replaced. Tested and system is getting a 22 temp split in air flow. Checked ac. Still running
Performing maintenance on a 2005 Goodman air conditioner.
2007 comfortmaker air conditioner. Found voltage absorption system dead on fan side. Compressor is running when calling for cooling. Condenser coil layered with dirt. Offered options on age hn5 for repair and cleaning. Customer chose Hn5b to have unit cleaned and repaired. Replaced voltage absorption system and cleaned unit. 18 degree temp drop. Let customer know it could take up to 24 hours to cool the home. All okay at this time.
Unit blowing warm air. Found unit low on refrigerant charge. System has developed a small leak. Offered options on page hj2 and option for replacing air conditioning system. Customer chose hj2a to charge system and restore cooling. Customer will call us when ready for estimate to replace. Charged system to 25 degrees sub cooling. Temp drop is 20 degrees. 90 degrees in the house, let customer know system will most likely run the rest of the day.
Customer has a heat pump system. Found thermostat wired and configured incorrectly. After rewiring and configuring thermostat outdoor unit would not run, found unit completely of refrigerant charge. System is 24 years old. Offered options for repair on page hl2 as well as for replacement of system, customer said he needs to hold off for now he is out of state and just bought the house. Let him know to call us when ever he is ready.
2016 Lennox air conditioner not cooling. Found unit low on refrigerant charge. Tested for leaks at joints and Schroeder valves and found no leak. Charge unit to 11 degrees sub cooling. Unit is now cooling the home.
Ac check on Bryant 2011. 14-25-1
Customer without cooling. Found bad thermostat wire from control board inside furnace to air conditioner. Replaced wire to restore cooling, also performed maintenance on the 1994 Lennox air conditioner and found the capacitor needed replaced to prevent a breakdown during the summer. air conditioner repair in galloway, ohio.