Providing 100% Relief Since 1950!
Located a few miles outside of the outer belt on the west side of the city, Galloway, Ohio was built on land that was originally owned by a Revolutionary War veteran. The area is known for it’s vast farming land and parks including Battelle Darby Creek Metro Park.
Sears Heating & Cooling is proud to be the dependable name for HVAC repair in Galloway, Ohio. Find out why we’ve been held in such high esteem since we were founded in 1950 from our local reviews below.
Common HVAC Repairs
Although there are many different things that can go wrong with your heating and cooling system, there are several issues that we deal with more than others. These troubles include strange noises or smells, no hot or cold air being produced or water leaks inside. Be sure to check your filter on a regular basis to ensure it’s not contributing to the problem. The number one cause of HVAC breakdowns is dirt and debris.
Are Your Repairs Warrantied?
Of course! Each heating and cooling repair that we complete comes with a warranty to give you peace of mind. The length of warranties offered range from 30 days all the way up to 2 years.
for Galloway, OH
Our Reviews by City
Harry - Galloway, OH
Josh was great
Response from Sears Heating & Cooling:
Thank you for your review!
Unit blowing warm air. Found unit low on refrigerant charge. System has developed a small leak. Offered options on page hj2 and option for replacing air conditioning system. Customer chose hj2a to charge system and restore cooling. Customer will call us when ready for estimate to replace. Charged system to 25 degrees sub cooling. Temp drop is 20 degrees. 90 degrees in the house, let customer know system will most likely run the rest of the day.
Customer has a heat pump system. Found thermostat wired and configured incorrectly. After rewiring and configuring thermostat outdoor unit would not run, found unit completely of refrigerant charge. System is 24 years old. Offered options for repair on page hl2 as well as for replacement of system, customer said he needs to hold off for now he is out of state and just bought the house. Let him know to call us when ever he is ready.
2016 Lennox air conditioner not cooling. Found unit low on refrigerant charge. Tested for leaks at joints and Schroeder valves and found no leak. Charge unit to 11 degrees sub cooling. Unit is now cooling the home.
Ac check on Bryant 2011. 14-25-1
Customer without cooling. Found bad thermostat wire from control board inside furnace to air conditioner. Replaced wire to restore cooling, also performed maintenance on the 1994 Lennox air conditioner and found the capacitor needed replaced to prevent a breakdown during the summer. air conditioner repair in galloway, ohio.