Sears Heating & Cooling has been the go-to name in Columbus, OH for everything HVAC related since 1950. We have repair and replacement options to fit any budget. Check out some of our local Columbus, Ohio reviews below!
A few reasons you may want to replace your HVAC system rather than repair it include:
- Your HVAC system is over 15 years old.
- Your HVAC system breaks down often.
- Your energy bills have drastically increased.
Another reason you may want to replace your HVAC system rather than repair it is if the cost to repair your equipment is more than the cost of having it replaced. To get your HVAC system repaired or replaced, contact us today.
It costs around $5,000-$10,000 to replace an HVAC unit in Columbus, OH. The price can be affected by:
- The size of your home.
- The type of HVAC unit you have installed.
- The cost to remove your current HVAC unit and install the new unit.
The overall cost can increase if you also need to have your existing ductwork replaced with new ductwork during the HVAC installation. To learn more about getting your HVAC system replaced, give us a call today.
To finance a replacement HVAC system in Columbus, OH, you can:
- Finance through your HVAC contractor.
- Get a loan through the Federal Housing Administration.
- Take out a home equity loan through your bank.
It can be very advantageous to finance through your HVAC contractor to keep your payments at a set rate each month to make purchasing your HVAC system more affordable. To find out more about financing for your HVAC system, call us today.
You can expect the cost to replace an AC capacitor near Columbus, OH to be in the range of $120 - $475. It’s a pretty quick project and usually takes less than an hour when performed by an HVAC expert, so costs should not go much higher than this.
If you were quoted a price greater than this range, get another quote from Sears Heating & Cooling. (And of course, we’ll give you a first-time quote.) We are well-known in the Columbus, OH area for our honest, professional work. Replace your air conditioner’s capacitor with an HVAC company you can trust!
for Columbus, OH
Our Reviews by City
Anita - Columbus, OH
Technician was very friendly and knowledgeable. Great experience.
Estimate on New System
Joe - Columbus, OH
Josh was very thorough and answered all my questions. I feel better prepared to make sn informed decision.
Professional HVAC Detective saved my life!
Another satisfied customer! - Columbus, OH
My experience with the Sears team has been excellent! I first learned about Sears through my next-door neighbor who has a recent full HVAC install. My neighbor also shared her Mother and Dad have been customers since the 1950's. It is this strong devotion to excellent customer service and professionalism that has kept my neighbor and her family coming back to Sears year after year! Service after the sale is not dead with this organization! I had been having some crazy high bills over the years even before the recent Columbia Gas rate hikes and grew even more concerned over the years when I began to have strange symptoms whenever I was at home. I always felt better away from my home when I was working at the hospital. I now believe it has been low-grade symptoms of CO poisoning- as a healthcare provider I should have put this together sooner! My tech Josh was immediately able to diagnose a cracked heat exchanger that when damaged can leak CO into living spaces or start a fire. He also discovered the capacitance system is below specifications due to poor install from another company- another efficiency and safety hazard. Josh basically with his detective work saved my life from CO poisoning and possible fire as the units in my building had NEVER been serviced by the owner since 1999 install. I am so deeply grateful to Josh and his company. Also, all of my work with the office team and even VP Bryan Meier has been deeply satisfying. This is a company and team that simply loves what they do with a team they love as family- I even feel like they treated me as a family member. If I could give all the stars from heaven for this review I would do it!
Louis - Columbus, OH
John did a great job explaining all issues and delivering cost effective solutions.
Paul - Columbus, OH
Josh always provides great service and really helpful information about our gas fireplace. He makes regular maintenance and repairs a wonderful service experience.
G - Columbus, OH
Josh is very competent and a pleasure to work with!
Daniel - Columbus, OH
Cody, was very professional and engaging. He was really thorough and patient about what he was doing and why. That young man (Kody), also have me very interested in purchasing a furnace surge protector….I’ll be calling the office soon about scheduling an appointment to get one installed. He should be considered a valuable asset to your company. Respectfully, Daniel
Overly charged for service
Frank - Columbus, OH
The furnace part replaced costs only $25 at most, but Cody charged me $269 plus $79 for coming in to check the problem. This is highway robbery!
Response from Sears Heating & Cooling:
Hi Frank-I'm sorry you feel this way. The price you paid is the cost for us to send a fully licensed and trained tech in a fully stocked truck (on a weekend no less) to your home to fix your furnace. You could have declined the price if you did not agree with it. If we only charged $25 for a repair, we would not be able to pay employees let alone offer them healthcare for them and their families. I would encourage you to call around to other local HVAC companies and compare pricing as I assure you that we are competitive, otherwise we would not still be in business after 72 years. The cost you paid covers the parts, labor, company overhead and a 10% profit. I think 10% profit is fair for the service we provide. Thanks for your comments and we wish you the best in finding another HVAC company that suits your needs.
Thank you for the service!
Karen - Columbus, OH
Very thorough and professional service
Steve - Columbus, OH
Josh was great. He answered all my questions and provided very good advice on a new system we plan to do next year.
Job Well Done
Michael - Columbus, OH
Nice guy, gave me the details I needed to make an informed decision, did the work thoroughly and quickly, easy to work with. Good experience.
James - Columbus, OH
Service call placed and someone was out within a few hours. Love Sears HC! They have great installers and awesome customer service.
Debbie - Columbus, OH
Josh arrived at the time he said he would. He was very nice and professional. He did a good job explaining what was wrong with my AC and fixed it in a very timely fashion. It was greatly appreciated since it was miserably hot outside! I also really appreciate him not trying to “upsell” -I would definitely have him come back if I needed assistance again
Dan - Columbus, OH
Josh came out to diagnose my AC not kicking on. He quickly traced the issue, and cleaned the outside unit and did a little upgrade to help reduce west and voltage on startup. Very professional and friendly. Would highly recommend him and Sears H&C!
Maria - Columbus, OH
Josh was great. He was very quick and explained what he was doing thoroughly. I felt that he was honest and he was also great with our dog!
Conducted AC cleaning on a 2003 carrier air conditioner. All mechanical components of the system check out find this time. Technician observed the outdoor capacitor outside of manufacture specifications. Technician presented options HN13 a through E. Customer chose option B. Technician conducted repair and system tested fine at this time. Technician discussed getting customer on maintenance plan to which they said they will call the office at a later point. Technician also discussed air cleaning product (eye wave) With tenant of the Home who said he will do research and get back with technician about purchasing
Ac maintenance inspection all systems operating at this time. Cleaned condenser coil and cycled equipment to ensure proper operation.
Replaced failed capacitor on a Goodman air conditioner.
Replaced fuse in service disconnect on an Armstrong air conditioner
Found ac system not operating due to insufficient refrigerant. Refrigerant leak test to be performed.
Air conditioning system needs Nitrogen leak lest to find link.
Repaired leak at outside unit triple vacuolated system improved electrical equipment recharge system return unit to service
Conducted annual maintenance on a 1998 Bryant air conditioner. All electrical mechanical components of the system check out of this time. Technician took measurements for condenser pad. Those measurements are 33 x 33. Technician collected both service contract and future repair today.
Cost to add air conditioning to a house without it. First time air conditioning cost of installation
Upon arrival customer stated issues have occurred since changing thermostat a couple days ago. Technician performed diagnostic steps to find fuse popped. Presented options SH6A-E customer chose option A to address concerns. Technician installed new fuse and cycled unit. No shorts at this time. No further concerns at this time unit running with 20 degree temperature drop
Left eestimate for new equipment as old has failed.
Performed furnace maintenance and safety check on American Stsndard unit. Left estimate for furnace & AC unit
Perfomed yearly maintenance and safety checks on 2 air conditioning units. See notes for individual checklist no concerns at this time. Service Club Safety & Performance AC Tune Up Bryant air unit. Check Stat. Does unit come on?: yes Did you change filter?: . No What size is the filter?: - 213 Temperature Drop: Return Air Temp: - 72 Supply Air Temp: - 50 Checked condensate drain line?:yes Did you turn the humidifer off for summer?: yes Does the evaporator coil have a TXV or fixed restrictor?: fixed Manufacture Date: -98 Refrigerant type:R-22 Outdoor Temperature: - 65 Voltage distribution system rating/actual rating: 35/5——35/5 Did you check the voltage distribution system for pitting/burning?:yes Start up Amps: Start up Amps: - 53 Cleaned condenser coil?: yes Check air movement system operation?: yes Returned furnace to service?:yes Does the customer have a Humidifier?:yes Does the customer have a APCO Light?:no Does the customer have a Leak & Freeze detector?:no Is there a sticke
Perfomed yearly maintenance and safety checks on 2007 York air conditioning system. Unit is running properly and within manufacture specifications at this time. No concerns at this time.
Provided estimate for mini split system for whole house
Upon inspection technician observed the drain piping loose right off of the coil T. Technician tightened the drain piping and the leak stopped. No further issues at this time.
Returned for leak search, found leak in evaporator coil, leak is in a location that cannot be fixed called supplier to get quote for new coil, there are currently no replacement coil options for system. Leak seal is not a good option for equipments microban coil. Informed customer of findings. Customer stated she will review options for replacement system with son and call us back if decision is made,
Reran new condensate drain tube from heating /cooling equipment to floor drain
Conducted annual maintenance on a 2018 Bryant air conditioner. All mechanical components of the system check out at this time. Technician observed initial amp draw just outside manufacture specifications. Technician presented options HN1 A-E. Customer stated she wanted to wait until next year to do the repair. Customer stated that During the furnace check she might want to have the thermostat replaced. No further issues at this time
Ac maintenance inspection all systems operating at this time.
Performed furnace maintenance and safety check on aRheem unit. Diagnosed faulty defrost control board.
Conducted annual maintenance on a 2016 Bryant air conditioner. I’ll mechanical electronica components of a system check out at this time.
Conducted annual maintenance on a 2019 Bryant air conditioner. All mechanical components of the system check out at this time. Technician observed compressor amp draw outside manufacturers specifications. Technician presented options HN18 a through E To the customer. The customer decided to pass on repair at this time, stating to keep an eye on it for next year to see if the problem progresses.
Conducted annual maintenance on a 2016 Rheem air conditioner. All electronica and mechanical components of a system check out at this time. Technician collected for the service club renewal today as well.
Conducted annual maintenance on a 2000 Rheem air conditioner. All mechanical components of the system check out of this time. Technician observed initial amp draw from compressor on the borderline of the manufacture specifications. Technician Presented options HN1 a through E, but due to the age of the unit the customer decided to wait on the repair.
Conducted annual maintenance on a 2003 carrier air conditioner. All mechanical components of the system check out at this time. Technician noticed amp draw outside of manufacture specifications. Technician present Options HN1 A-E. Customer stated due to the age of the unit he did not want to follow through with repair at this time.
Replaced failed capacitor on a Comfortmaker air conditioner
New install April 2022, technician found discount in off position, flipped disconnect to on position. Unit started up properly. Customer stated installer stated wire will come back to add refrigerant due to ambient temperature. Technician found unit running at 18 degree delta t. No further concerns
Completion Notes: Upon arrival thermostat set to off position. Tech made call for cooling, unit cycled on properly without fault. Technician found unit running at 3 degree temperature drop. Performed electronic leak search, found no hits of refrigerant outside. Technician found Hits inside near evaporator coil. Coil replaced under warranty in 2016. Informed customer of findings and went over options.Customer chose to have sealant installed on air conditioner as well as having hard start installed on unit. Technician presented options hj7C-E to address concern. Customer chose option C. Technician performed repair. Cycled system to ensure operation. System running at 20 degree delta t
Technician made call for cooling, indoor unit cycled properly. Contactor was pulled but unit wasn’t starting, found fuse inside disconnect bad only sending one leg of power to system. Replaced fuse. System cycled on properly and ran with a 17 degree temperature drop no further concerns at this time.
Conducted A routine cleaning on a 2019 comfort maker air conditioner. All mechanical components of the system check out at this time. Technician observed voltage distribution system slightly out of manufacturers specifications. Technician presented options HN1 A-E To the customer. The technician also presented the maintenance program to customer. Customer stated that due to the uncertainty of the future of the house he declined both the maintenance program and the possible fault correction. Nothing else to note at this time.
Performed air conditioner maintenance and safety check on Bryant unit
2010 carrier air conditioner. Found condenser fan motor failed due to open windings. Compressor had run without the fan for a long period of time. Recommended adding performance kit to assist compressor on start up. This will reduce inrush current and extend compressor life. Went over options on hc8. Chose hc8b. Replaced failed motor, updated voltage enhancing system for fan. Installed performance enhancing kit for compressor. 50 amps for compressor start up and sounds very good when running. Temp split is 18 degrees. All okay at this time.
Performed yearly maintenance and safety checks on 2019 Comfortmaker air handler heat pump system. System is operating properly and within manufacture specifications at this time. No concerns at this time
Performed air conditioner maintenance and safety check on American Standard unit
Conducted annual maintenance on a 2011 air conditioner. All mechanical an electronica components of the system check out this time.
Replaced faulty condenser fan motor